Not sensing any heat and noticing error code 228 from your Lennox® furnace?
This indicates your heating system couldn’t adjust its pressure switch before launching. As a result, your system will not run for your safety.
Repairing or replacing this part is best left to the technicians at Service Experts Heating & Air Conditioning in Kingston. Our NATE-certified technicians are among the brightest in the industry. They’re well-prepared to take care of all of your heating needs, including fixing a furnace error.
We want you to be absolutely satisfied with our quality furnace repair in Kingston. That’s why we back it with a 100% Satisfaction Guarantee* for a year.
How a Pressure Switch Works
This part plays a critical part as your furnace prepares to work in your space.
Here’s what happens after your thermostat’s call for heat:
- Your furnace’s control board commences running the draft inducer blower motor. This exhausts combustion gases from the heat exchanger and moves in new gas and air so the burners can fire.
- When the pressure switch senses that plenty of air is being pulled into the burners, it closes and tells the control board to ignite the furnace.
- Your furnace ignites and creates heat.
What Happens When a Pressure Switch Breaks Down
When your pressure switch isn’t working the way it should, you’ll likely hear the fan start and the switch clicking a couple times before the furnace turns off completely. When a part isn’t working right, your furnace will turn off as a safety precaution.
Your furnace will show you something is wrong with a red flash from its indicator light, which it uses to exhibit error codes. It uses this red light to flash code, like Morse code.
You may note fast flashes or an alternating slow flash as it passes on a fault code.
Estimated Repair Cost for Furnace Error Code 228
Before replacing the switch, your Service Experts Heating & Air Conditioning tech will check other parts of your furnace first. A handful of other issues can also generate the error code, like a clogged vent or cracked hose.
The bill to repair your furnace depends on what’s wrong with it and how long it takes to fix it.
If your pressure switch needs to be replaced, you can anticipate to pay between $40 to $350.
Trust the Experts at Service Experts Heating & Air Conditioning
If you should have furnace repair, trust the pros from Service Experts Heating & Air Conditioning to understand the fault code and fix the problem to your requirements.
Call us at 613-817-1591 or schedule an appointment online today.